We all know that the front and rear water chambers of the condenser
are the rubber ball gathering station and the transfer station. Their structural design should consider eliminating dead balls as much as possible.In addition to the water chamber designed as an arc-shaped ball and a cylindrical cavity, an arc-shaped deflector can be added. Grid and so on. In addition to the rubber ball cleaning device, the condenser of the power plant has also added three electric butterfly valves to constitute the backwashing device.Therefore, the front water chamber has a rectangular structure, while the left and right rear water chambers have arc-shaped structures, The two rear water chambers are connected to two connecting pipes of 600 each, and two large vortex ball dead zones are formed in the interface area, and some rubber balls are gathered in the pipes in the intersecting zone. .
The editor of Ruicheng put forward an improvement plan for adding a grille, and persuaded the improvement plan to the manufacturer's design engineers several times. Eventually, it was adopted by the factory and implemented on the site. The ball collection rate of 4 sets of rubber ball cleaning devices of the two machines has been kept above 95%, and imported rubber balls are used. The chambers are all arc-shaped structures, and there is no large dead zone in the water chamber, so there is no need to add deflectors. It is worth mentioning that the above three power plants have a very low ball collection rate when using domestic rubber balls, and severe ball accumulation in the
water chamber after the occurrence of power balls. The quality problem was later changed to the imported rubber ball test. The above problems no longer existed, thus naming the condenser.