The rubber ball cleaning device is one of the important means to improve the operation efficiency of the power plant at this stage. The on-line condenser rubber ball cleaning system has become the standard equipment of the power plant. The quality of the rubber ball is one of the key elements of the system. Should be selected for wear resistance, soft texture and rich elasticity, uniform material, moderate hardness, uniform air and air penetration, wet specific gravity of 1.0-1.15, under the water temperature of 5-45 ℃, the inner diameter of the ball does not exceed the standard during the use period, not aging.
The ball loading chamber is a device for adding, receiving, changing, and investigating the operation of rubber balls in the condenser rubber ball cleaning system. There are two types of JZ-Ⅰ and JZ-Ⅱ, JZ-Ⅰ is used for units below 125MW, and JZ-Ⅱ is used for units above 125MW. The position of the device should be easy for the operator to access and operate. The diverter is a three-way valve. By switching the guide plate, the rubber ball can enter the condenser that needs to be cleaned to work. Generally one unit requires two distributors. The inlet diameter is DN100 and the distribution port is DN80. When the rubber ball is put into use, the operation can be investigated through a viewing window. Condenser rubber ball cleaning system The rubber ball delivery pump is an obstacle-free pump. This pump will not damage the rubber ball during operation, and its pump efficiency is high and the life is long.
Article from: http://wfzljs.com/chanpin/